Mécanique & Industries
Volume 12, Number 5, 2011
|Page(s)||409 - 418|
|Published online||04 November 2011|
Balancing with the presence of a rub
GE Energy Measurement and Control Solutions, 2 rue de
La Chapelle sur Erdre,
a Corresponding author: email@example.com
Received: 16 June 2011
Accepted: 26 July 2011
During commissioning of a cogeneration plant the air cooled generator cannot be run up to synchronization speed because of high 1X vibration during startup. Several attempts were done by the commissioning team to balance the rotor but proven ineffective. This paper presents the vibration analysis performed by GE MDS Engineer. As a result of the analysis it was concluded the high levels of synchronous vibration are caused by thermally induced bow because of rub in the new type of seals installed in generator casing. The seals were removed for test and the generator was started successfully. The next part of the paper discusses the differences between Newkirk and Morton type thermally induced bows as they can be observed in the machinery diagnostics during field analysis.
Key words: Rubbing / balancing / rolling phase / thermal phenomenon / Newkirk / Morton effect
© AFM, EDP Sciences 2011
Current usage metrics show cumulative count of Article Views (full-text article views including HTML views, PDF and ePub downloads, according to the available data) and Abstracts Views on Vision4Press platform.
Data correspond to usage on the plateform after 2015. The current usage metrics is available 48-96 hours after online publication and is updated daily on week days.
Initial download of the metrics may take a while.